Our life teaches us the truth of being human and doing things. Some people often make a fuss about things and are not calm. However, some people can often overcome their fears, calm down and find solutions to difficulties. We need to calm down when the diesel straw gas generator set fails in the process of using the diesel straw gas generator set. Find out the cause of the unit failure and eliminate the failure. There is no need to make a fuss. You can also solve the small fault of the straw gas generator set.
1. Thermostat damaged
If the water temperature of the straw gas generator set is too high, it is generally due to the failure of the thermostat, which slows down the large circulation flow rate of the coolant, and you need to purchase a new thermostat to replace it.
2. Solution to Fan Belt Cracking
If the fan belt of the straw gas generator unit is damaged, it should be stopped immediately for replacement. If there is no condition for further replacement, two small holes can be drilled at both ends of the fracture of the original fan belt, and then thick metal wire can be used to connect the broken belt for emergency use. It should be noted that proper spacing should be kept between the drilling hole and the section to prevent the hole from being pulled apart. The joint of the metal wire should be left at the outside of the belt, and the belt should not be adjusted too tightly. If the fan belt is severely damaged and cannot be connected, the rope, cloth belt and leather belt can be fastened with iron wire to form a belt for temporary use. Special attention shall be paid to the length and thickness of the belt, which shall be equal to the original belt, and the rope head shall be clamped in the center and tied.
3. Radiator water pipe leaks
During the use of the straw gas generator set, the water temperature inside the radiator pipe is too high and the external temperature is too low. Or because of the vibration of the straw gas generator set, it is easy to cause water leakage of the water tank pipe. If the water tank of the straw gas generator set leaks, the loose cut tobacco can be put into the water tank, and the pressure of water circulation can be used to block the cut tobacco at the leaking place of the radiator pipe for temporary use. If the water leakage of the radiator pipe of the water tank is serious, the water leakage can be cut off, and then the cotton ball is coated with soap at the cut radiator pipe, and then the head of the cut radiator pipe is clamped flat with pliers, and then the water leakage can be stopped by crimping and pressing.
4. Water pump leaks
The straw gas generator set uses aluminum water pump, sometimes the seal is not tight. The plane of the water seal shall be polished flat, or the water seal shall be turned 180 ° before installation and operation. If the thrust rubber ring is damaged, swollen or deformed, or the tension spring is short of elasticity or broken, it should be replaced, and the tension spring should not be pressed to death during installation.
The above is a detailed introduction to the refining tail gas generator set, and I hope it will be helpful to you. If you have any questions, please contact us. We will provide you with professional services https://www.huannengpower.cn