The natural gas generator set is the emergency power supply after the urban power failure. Most of the time, the natural gas generator set is in standby state. Once the power failure occurs, the unit is required to "emergency start, emergency power supply" immediately. Otherwise, it will be meaningless as a natural gas generator set. How can we ensure that the natural gas generator set can maintain the normal power generation state in an emergency? Therefore, it is necessary to strengthen daily maintenance, because the natural gas generator unit is in a long-term static state, and various substances of the unit itself will undergo complex chemical and physical changes with oil, cooling water, diesel oil, air, etc., thus causing the unit to "shut down poorly".
The occurrence of many serious failures is often due to the failure of daily maintenance; Or a small fault occurs and the user does not pay attention to it, which, in the long run, leads to the failure of the natural gas generator unit to work normally. In the daily inspection of natural gas generator units, it is difficult for non professionals to find some small traces, which usually leads to major failures of the generator units and can not be used. It was not found that the equipment could not operate until the natural gas generator set was started in an emergency. After the repair was reported, the maintenance personnel arrived to determine the failure, determine the maintenance plan, and then began to purchase accessories for maintenance until the end, at least 10 days or half a month later, the losses caused were irreparable. The starting battery is the basis to ensure the normal startup of the natural gas generator set. Nearly 30% of the failures in the failure to start the generator set are caused by the failure of the starting battery of the unit, for example, the battery has been left unattended for a long time, and the electrolyte water cannot be replenished in time after volatilization; No starting battery charger is configured; The electric quantity of the battery decreases after natural discharge for a long time; Or the chargers used need to be manually and regularly switched for equalizing/floating charge, and the battery power fails to meet the requirements due to negligence. The daily maintenance and overhaul of natural gas generator units is very important, especially in summer and winter, when the ambient temperature deviation is too large.
The above is a detailed introduction to the biomass gas generator set, and we hope it will be helpful to you. If you have any questions, please contact us. We will provide you with professional services https://www.huannengpower.cn